Payment & Shipping Terms:
|Name:||Plug Stab Fingers||Current:||0-100A|
|Busbar Size:||4/5mm||Other Name:||Bus Plug Stab Finger|
ISO9001 400A plug in contact,
ISO9001 Busduct Contact,
Kiande plug in contact
Female Busbar Copper Pins for Busduct Plug in Contact Box
|KDT-15-5||0-100A||4/5mm||Compact busbar plug||T Type|
|KDT-18-5||100-200A||4/5mm||Compact busbar plug||T Type|
|KDT-22-5||250-350A||4/5mm||Compact busbar plug||T Type|
|KDT-30-5||400-630A||4/5mm||Compact busbar plug||T Type|
|KDT-15-6||0~200A||6mm||Compact busbar plug||T Type|
|KDT-18-6||250-350A||6mm||Compact busbar plug||T Type|
|KDT-28-6||400-630A||6mm||Compact busbar plug||T Type|
|KDF-125||0-125A||19 phase distance,
22 phase distance,
26 phase distance above
|Air busbar plug||F Type|
|KDF-160||125~160A||Air busbar plug|
|KDF-250||160-250A||Air busbar plug|
|KDF-630||315~630A||Air busbar plug|
Busbar Trunking System is the is a system of distributing electric power using copper or aluminium busbar with suitable enclosures and good amount of protection to prevent the cables from getting damaged due to foreign bodies. ... The system of cooling is much better than traditional cabling system.
Installation Guideline of Tap Off Unit (Plug-In Type)
There are two types of plug-in tap-off units :
1) Plug-in tap-off units without automatic clamping system .
2) Plug-in tap-off units with automatic clamping system.
Step 1: Open or remove the tap-off unit cover.
Step 2: Install the protection device in the tap-off unit.
Step 3: Remove the IP protection on the outlet of the run component.
Step 4: Prepare the output cable glands and connect the cables to the tap-off unit.
Step 5: Check that the protection device is switched off and carefully inspect the tap-off unit for tools and objects that may have been left inside the tap-off unit.
Step 6: Position the rear of the tap-off unit on the run component.
Step 7: Plug the tap-off unit into the run component.
Step8: Lock the tap-off unit on the run component using the locking handle located inside the tap-off unit
Step9: Secure the tap-off unit on the run component using the fixing mechanism.
Step10: Close the tap-off unit cover. The system and the load are ready to be energized.
Contact Person: admin