Payment & Shipping Terms:
|Type:||Compact Busbar Plug||Material:||Copper|
Female Copper Tob Busbar Plug,
5mm Tin Busbar Plug,
Female Copper Tob Busbar Accessories
Female Copper Tob Contact Leg Tin For Busduct Plug In Contact Box
|KDT-15-5||0-100A||4/5mm||Compact busbar plug||T Type|
|KDT-18-5||100-200A||4/5mm||Compact busbar plug||T Type|
|KDT-22-5||250-350A||4/5mm||Compact busbar plug||T Type|
|KDT-30-5||400-630A||4/5mm||Compact busbar plug||T Type|
|KDT-15-6||0~200A||6mm||Compact busbar plug||T Type|
|KDT-18-6||250-350A||6mm||Compact busbar plug||T Type|
|KDT-28-6||400-630A||6mm||Compact busbar plug||T Type|
|KDF-125||0-125A||19 phase distance,
22 phase distance,
26 phase distance above
|Air busbar plug||F Type|
|KDF-160||125~160A||Air busbar plug|
|KDF-250||160-250A||Air busbar plug|
|KDF-630||315~630A||Air busbar plug|
Installation Guidence of Busduct Joint
Step1:dentify the correct joint stack (either 4W or 5W) and its phase orientation before Busduct joint pack installation
Step2: Align and connect both busduct terminal with joint stack connector.
Step3:Joint stack stopper acts a guideline to ensure a full contact surface of the overlapping conductors.
Step4: Tighten the double headed bolt by using socket wrench untile the outer head shear off.
Step5:Place joint pack covers on both sides of the busduct joint section and tighten all the bolts and nuts with socket wrench.
Busbar Trunking System is the is a system of distributing electric power using copper or aluminium busbar with suitable enclosures and good amount of protection to prevent the cables from getting damaged due to foreign bodies. ... The system of cooling is much better than traditional cabling system.
Contact Person: Tina